The FIL-ANN80 is made to fit any of the Fire-Lite Fire Panels and it is an 80 character LCD Fire Annunciator.
This is basically a remote version of the display panel on the actual Fire-Lite panel itself and will display the following conditions:
- AC Power
- Alarm Silenced
This communicates to the main panel via a two-wire serial interface and uses the ANN-BUS communication protocol.
Operating voltage range: 18 VDC to 28 VDC.
Current consumption @ 24 VDC nominal (filtered and nonresettable):
40 mA maximum.
Ambient temperature: 32°F to 120°F (0°C to 49°C).
Relative humidity: 93% ± 2% RH (noncondensing) at 32°C
± 2°C (90°F ± 3°F).
5.375 (13.65 cm.) high x 6.875 (17.46 cm.) wide x 1.375
(3.49 cm.) deep.
For use indoors in a dry location.
All connections are power-limited and supervised.
Listed to UL Standard 864, 9th Edition.
Backlit 80-character LCD display (20 characters x 4 lines).
Mimics all display information from the host panel.
Control switches for System Acknowledge, Signal Silence,
Drill, and Reset.
Control switches can be independently enabled or disabled
at the FACP.
Keyswitch enables/disables control switches and mechanically
locks annunciator enclosure
Keyswitch can be enabled or disabled at the FACP.
Enclosure supervised for tamper.
System status LEDs for AC Power, Alarm, Trouble, Supervisory,
and Alarm Silence.
Local sounder can be enabled or disabled at the FACP.
ANN-80 connects to the ANN-BUS terminal on the FACP and
requires minimal panel programming.
Displays device type identifiers, individual point alarm, trouble,
supervisory, zone, and custom alpha labels.
Time-and date display field.
Surface mount directly to wall or to single, double, or 4"
square electrical box.
Semi-flush mount to single, double, or 4" square electrical
box. Use ANN-SB80KIT for angled view mounting.
Can be remotely located up to 6,000 feet (1,800 m) from the
Backlight turns off during AC loss to conserve battery power
but will turn back on if an alarm condition occurs.
May be powered by 24 VDC from the host FACP or by remote
power supply (requires 24 VDC).
Up to eight ANN-80s can be connected on the ANN-BUS.